Sample of Previous Cases
Construction Defect: 280 Unit Condominium, Sacramento, CA.
Electrical Engineering Expert Witness, Identified electrical installation hazards sampling shown in the pictures.
- Fire Hazard; Receptacle set back too far from face of the sheetrock.
- Fire and Smoke Hazard; Romex wiring running through crawl space in attic not Fire Stopped properly.
- Shock Hazard; Air Conditioner condensing unit installed in front of safety switch and inadequate clearance between safety switch and condenser.
- West Lake Villas Community Assoc v. West Lake Villas, LLC, Bohm & Wildish Law, Defendant, James G. Bohm Esq.